Looking for heating or AC services near Jenkintown, PA? Chud provides air conditioning, heating, water heater and air quality services. We’ve been in business for more than 50 years.
When you’ve been around as long as we have, people know your name. See our reviews and find out why your neighbors consider us to be their nearby heating and air company in Jenkintown, PA.
for Jenkintown, PA
Our Reviews by City
Shlomo - Jenkintown, PA
Response from Chud Air Conditioning & Heating:
Thank you for the 5 stars, we appreciate it!
Abington Customer - Jenkintown, PA
Performed preventative maintenance for 3 air conditioning only units. Replaced the Merv 11 air filters on 2 of them (garage- 20x25x5 basement- 16x25x5). Cleaned the electronic air cleaner in the first floor bedroom. Inspected all drains for blockages. Inspected all the electrical components. Tested the temperature splits on all the systems. All were at 20Â° differentials. The garage unit had super seal added last year and 4lbs of 410A found no signs of dye or loss of cooling ability. All systems are operating properly at this time.
Performed air duct cleaning and sanitation. All vents and ductwork are clear of dust and debris at this time. Unit is functioning properly at this time. Recommend duct cleaning every 2-3 years. Performed dryer vent cleaning. Dryer vent and duct is clear of lint and debris at this time. Dryer is functioning properly at this time. Recommend dryer vent cleaning every 1-2 years. Thank you for your business!
Completed air conditioning tune up on Lennox HVAC system. Inspected coils, drains tested, electrical components checked including amperage/voltage readings on compressor, capacitor and contactor. System ready for air conditioning operation. N/C, has M/A.
Performed air duct cleaning and sanitation. All vents and ductwork are clear of dust and debris at this time. We removed and old filter that was blocking the motor which was inhibiting the air flow. The furnace is functioning properly at this time. Recommend duct cleaning every 2-3 years. Thank you for your business!
Installed Bradford White 75 gallon gas direct vent hot water heater. Adapted to 3/4â€ copper water lines, reused ST-12 expansion tank and adapted to 3â€ PVC exhaust vent. Inspected for water/gas leaks. Quoted $3225.00. $100 discount per RC.
Replacing a blower motor
Performed preventative maintenance for air-conditioning system. Replaced the Merv 11 air filter (16x25x5). Inspected all the electrical components and controls. Inspected the gravity drain to condensate pump. The drain piping is clear and the pump is functioning as it should. Pump was replaced in 2019 with the furnace. Tested the temperature split between the supply and return. System is operating with a 19Â° differential. Went out to inspect the condensing unit. This system is an R 22 unit. Tested the amp draw from the compressor and the fan motor. Both are operating within manufacturer spec. Inspected the capacitor and contactor. Both are pretty worn but are working as they should at this time. System is operating properly at this time. This is a billout to Mr. & Mrs. Lukens.
Performed preventative maintenance for 2 air conditioning systems. Customer replaces the air filter for the basement unit (16x25x1). The attic unit has a Merv filter cabinet that had the wrong size air filter in it. Being that it only had a standard air filter but fits a Merv the customer wanted to upgrade to the bigger filter at the proper size. Installed a Merv 11 air filter (20x25x5). Inspected all the electrical components for both systems. Made sure both gravity drains were clear. Basement unit does have a condensate pump that works properly. Inspected all wiring for good connections and no exposed/damaged wires. Went out to the condensing units. Tested the amp draw from The compressors and fan motors. All were operating properly within manufacturer spec. Inspected the contactors and capacitors all are fairly worn but are still operating properly. Tested the temperature split between the supply and return. The basement unit had a 19Â° differential and the attic unit had a 20Â° dif
Access leaking hot water heater. Determined that the Bradford White 75 gallon gas power vent water heater will need replacement. Homeowner advised ST-12 expansion tank recently replaced on 09/21/20. Regular customer, diagnostic charge waived with agreement to replace tank.
Performed preventative maintenance for air conditioning system. This is an AC only unit with an air handler in the attic. Customer replaces the Merv air filter (20x25x5). Inspected all electrical components for proper voltage and amperage. Tested the temperature differential between the supply and return. Had an 18Â° split. Inspected the condensing unit. Tested the amp draw from the compressor and fan motor. Both are operating within manufacturer spec. Inspected the capacitor and contactor. Both are older but still in good condition. Looking inside the duct work and the return grille in the ceiling I noticed a fair amount of dirt and dust. Recommend having a duct cleaning to remove all dirt and sanitize the system. System is operating properly at this time. Customer also prepaid for duct cleaning that needs to be scheduled.