Want to breathe better air at home? Chud has been bringing excellent indoor air quality services to the residents of Norristown, PA and the surrounding areas since 1970! We also provide complete air conditioning and heating solutions.
See what your neighbors in Norristown, PA are saying about Chud’s indoor air quality expertise. We’ll clean your ducts and clean your air to help you have better health in your home.
for Norristown, PA
Our Reviews by City
***Rich, maintenance supervisor will call 04/09/21, or 04/12/21 to confirm. Must get approval from Property management 1st before ordering.*** Replace furnace, coil and condensing unit for townhome#3154. Flush lineset, adapt to existing 2â€ PVC venting system. Adapt to existing return drop. Has existing filter slot for 16x25x1 air filter. Install new Honeywell T4 thermostat. 1 year parts, 1 year labor and 5 year compressor warranty. (1)-GMES920804CN, (1)-CAPF3636C, (1)-GSX14036, (1)-Honeywell T4 Pro Series thermostat. Installation complete. Completed according to above specifications. Cycled and tested, system working properly at this time. BILL OUT
Apartment #4312. No ac call. Found contactor pulling in and out on start up. Determined that unit has a low pressure cut-off switch. Unit is about 5 years old R-410a. Charged unit with 2 lbs R-410a refrigerant today. Outdoor temperatures are in the low 40â€™s today. After charging unit ran consistently. Advised customer that refrigerant was added. BILLOUT. NATIONAL COMFORT GAS PACKAGE UNIT M#CPG41838-U12, S#35640968.
No heat call apartment #4524. Found inducer running, no ignitor, no error code. Determined pressure switch was not â€œmakingâ€ and checked port coming off of inducer housing. Port was completely clogged. Opened port by running a small drill bit through hole. System is operating properly at this time. BILLOUT. NATIONAL COMFORT GAS PACKAGE UNIT M#CPG42451-U11, S#35560087.