Chud has provided air conditioning, heating, water heater, air quality and duct cleaning services to the residents of Holland, PA and the surrounding areas since 1970! We’re committed to providing first class air conditioning service to all of our clients.
We’re the AC experts. But don’t take our word for it. Check out our reviews and find out why your neighbors consider us to be their nearby Holland, PA heating and air company that specializes in air quality and duct cleaning.
for Holland, PA
Our Reviews by City
Customer called for no heat. This is a landlord/tenant situation. Upon inspection I found a code at the heat pump for low pressure lockout. Hooked my gauges up to the system and found very little refrigerant charge left. I then opened up the cabinet for the evaporator coil to look for any residual oil in the drain pan. Found a good amount of oil in the drain pan and used some leak tester liquid to confirm. Found a heavy leak in this coil. System is 7-8 years old and has 2 options to fix the issue. Basic option is to replace the evaporator coil and refrigerant. This will get it back up running without a leak but is a major costly repair. Preferred option is to replace the system with a new heat pump and indoor air handler. This is preferred due to the high cost repair is 40%+ of a new system. Will need to hear from the customer on which way they would like to move forward. System can operate on electric heat only for the time being until the repair is decided on. Explained to tenant on
Performed air duct cleaning and sanitation on a 4 bedroom single system house. All vents and ductwork are clear of dust and debris at this time. System is functioning properly at this time. Recommend duct cleaning every 3-4 years. Performed a first floor dryer vent cleaning. Dryer vent, duct, flex hose and lint trap are all clear of lint and debris at this time. Dryer is functioning properly at this time. Recommend dryer vent cleaning every 1-2 years. Thank you for your business!
Installed new Lennox OEM condenser fan motor for existing Lennox heat pump. Reused fan blade and installed new 35/5MFD dual capacitor. Tested unit for proper operation. Homeowner had a new 20x20x1 air filter which was installed during the repair today.
On arrival found tripped breaker. Reset breaker. Found failed condenser fan motor. Advised landlord that fan motor will need to be replaced. Quoted customer on repair and created “sold” estimate in Service Titan.
Performed preventative maintenance for heat pump system. Customer replaces the air filter. Inspected all the electrical components. Confirmed proper high and low voltages. Tested the amp draw of the blower, compressor and fan motor. All are operating within the manufacturer specs. Found the Honeywell UV light not working. This is due to bulb being burned out. Replaced bulb since I had one available on the truck. Tested that the system would go into defrost. System had a temp rise of 55° system is operating properly at this time. Customer asked for senior discount as well.
Performed rooftop dryer vent cleaning. Dryer vent, duct, flex hose, motor and lint trap are all clear of lint and debris at this time. Dryer is functioning properly at this time. Recommend dryer vent cleaning every 1-2 years.
Performed rooftop dryer vent cleaning. Dryer vent, duct, flex hose and lint trap are all clear of lint and debris at this time. Dryer is functioning properly at this time. Recommend dryer vent cleaning every 1-2 years.